EEV opening         %          1   1   1   A   17
EEV position        step       0   1   1   I   15
Act. SH set         K          1   1   0   A   10
Superheat           K          1   1   0   A   15
Ev.probe press.     barg       1   1   0   A   14
Ev.probe sat.temp   °C sat     1   1   0   A   16
Suction temp.       °C         1   1   0   A   13
Cond.probe press.   barg       1   1   0   A   12
Cond.probe sat.temp.°C sat     1   1   0   A   9
                      
µC2 off line                   0   2   0   D   24
50% capacity                   0   2   0   D   25
100% capacity                  0   2   0   D   26
Alarm Low SH                   0   2   0   D   41
Alarm MOP timeout              0   2   0   D   44
Alarm LOP timeout              0   2   0   D   45
EEV not closed                 0   2   0   D   47
Low SH status                  0   2   0   D   52
MOP status                     0   2   0   D   49
LOP status                     0   2   0   D   50
High Tc status                 0   2   0   D   53
Alarm Eeprom err.              0   2   0   D   42
Alarm probe err.               0   2   0   D   43
                   
CH-Superheat set    K          1   3   7   A   22
HP-Superheat set    K          1   4   7   A   23
DF-Superheat set    K          1   5   7   A   24
CH-Prop. gain                  1   3   7   A   25
HP-Prop. gain                  1   4   7   A   26
DF-Prop. gain                  1   5   7   A   27
CH-Integral time    s          0   3   7   A   28
HP-Integral time    s          0   4   7   A   29
DF-Integral time    s          0   5   7   A   30
CH-Low Superheat    K          1   3   7   A   43
HP-Low Superheat    K          1   4   7   A   44
DF-Low Superheat    K          1   5   7   A   45
LOP Cool Mode       °C sat     1   3   7   A   50
LOP Heat Mode       °C sat     1   4   7   A   51
LOP Defr. Mode      °C sat     1   5   7   A   52
MOP Cool Mode       °C sat     1   3   7   A   53
MOP Heat Mode       °C sat     1   4   7   A   54
MOP Defr. Mode      °C sat     1   5   7   A   55
              
Circuit/EEV ratio   %          0   6   7   I   20
Dynamic prop. gain  %          0   6   7   I   71
SH dead zone        K          1   6   7   A   32
Derivative time     s          1   6   7   A   31
Low SH int. time    s          1   6   7   A   33
LOP integral time   s          1   6   7   A   34
MOP integral time   s          1   6   7   A   35
Hi TCond.int.time   s          1   6   7   A   36
Hi TCond.protection°C sat      1   6   7   A   40
Alarms del. Low SH  s          0   6   7   I   52
Alarms del. LOP     s          0   6   7   I   53
Alarms del. MOP     s          0   6   7   I   54
MOP startup delay   s          0   6   7   I   49
Al. delay probe err.s          0   6   7   I   48
                                     
MODE                from µCH2  0   7   7   I   16
REGOLATION          from µCH2  0   7   7   I   200
Refrigerant                    0   7   7   I   50
EVD probes type                0   7   7   I   69
Valve type                     0   7   7   I   30
EEV mode man.       Yes/No     0   7   0   D   68
Requested steps     passi      0   7   7   I   62
Open relais low SH  Yes/No     0   7   0   D   60
Open relais MOP     Yes/No     0   7   0   D   61
Valve alarm         Yes/No     0   7   0   D   70
Aux reg.                       0   7   7   I   56
S1 probe limitsMin  barg       1   7   7   I   41
S1 probe limitsMax  barg       1   7   7   I   42
S2-Pt1000 calib.    ohm        1   7   7   I   68
Probes offset S1    °C:barg    1   7   7   A   1
Probes offset S2    °C:barg    1   7   7   A   2
Probes offset S3    °C:barg    1   7   7   A   3
En. reset to default14797      0   7   7   I   1
Reset to default    Yes/No     0   7   0   D   1
Standby steps       step       0   7   7   I   25
BlockedValve check  s          0   7   7   I   51
Go ahead            Yes/No     0   7   0   D   35
                         
[MODI REGOLAZIONE]
COOL - 1
HEAT - 2
DEFROST
COMMON

[TIPI REGOLAZIONE]
SUPERHEATING
SUPERHEATING
SUPERHEATING